1: select a valid steam pressure reducing valve,pressure to 0.6Mpa, ensure that the steamtemperature at 160 deg. This guarantee or heat exchanger.
2: use of asbestos pads or steel flangeinterface pad.
3: water side first, then openthe steam side, first off steam, then turn offthe water. Avoid dry, damaged pads.
4: the condensation water outlet choose calibertrap or not wear, and natural emissions of condensate from a low level, do not let thewater higher than the low export, so as to avoidthe steam side of poor drainage, steam cannotenter but not heat.
5: select a valid temperature control system(valve or solenoid valve), effective control of the water temperature and steam open, so as to avoid the water temperature is too high.
Abovemay cause damage to the heat exchanger rubbermat.